This checklist will be an aid to maintain quality design of Electrical Cable Routing.
|Verify Client Name
|Verify Project Title
|Verify Drawing Title
|Verify Drawing No. & Revision No.
|Verify Job No. (Project No.)
|Verify the reference drawing numbers and titles.
|Verify notes and legends
|Verify Match Line indicated correctly
|Is the latest piping plot plan drawing referred to?
|Is the scale appropriate to the size of the drawing?
|Are the size of characters suitable for drawing size and scale?
|Are the type and width of lines suitable for drawing size and scale?
|Is the location identification of the plant shown on the drawing indicated by North mark, key plan, etc.?
|Incorporate Client’s requirement such as direct burial, concrete duct bank, above ground cable tray system, etc.
|Make special consideration for cable route consider, where enhancement is required, such as at road crossing, area paved by concrete or asphalt.
|Consider suitable points/places of cable splice from view point of the maximum available cable length per one cable reel.
|Check the interference among the cable route and other obstacles such as piping, foundation of structure/column, etc.
|Check the provision of the appropriate number of man-holes allocated at suitable locations considering the maximum allowable side wall tension and pulling tension of the cable for the duct bank system.
|Show the detail of man-holes considering the required working space of cable installation, splicing and termination
|Show the location of cable route markers.
|Cross check single line diagrams, cable run, connection diagram, and cable schedule for cable information.
Read more: List of All Checklists