Resistance of cable conductor varies with ambient temperature. This cable resistance conversion calculation tool used to alter cable resistance from one temperature base to another in accordance to IEC 60228.
Formula for cable resistance conversion
Formula for cable resistance correction is as follows:
|Rt||:||Conductor resistance at temperature t oC|
|R20||:||Conductor resistance at 20oC|
Conversion factor kt will vary with temperature t and conductor material.
For annealed copper conductors (plain or metal coated):
For aluminium conductors:
Maximum conductor temperatures for different types of insulating material has been specified by IEC 60502.
The temperatures in above table are based on the physical properties of the insulation materials. It is important to take into account other factors (i.e. cable arrangement derating) when using these values for the calculation of current ratings.